Check to see if product is in stock:
The LineGard™ PGFM GFCI Sensing Module is a ground fault or equipment leakage sensing device designed and manufactured by North Shore Safety, a leader in innovative safety products.
The PGFM operates in tandem with an approved Airpax LEL Series, UL 489 listed circuit breaker, with shunt trip and auxiliary switch. The combined assembly is recognized as a Class A UL 943 rated device. The sensing module is available in models to operate at supply voltages of 120 VAC or 240VAC and can monitor single and split phase circuits.
These devices meet the requirements of OSHA 29 CFR1926.404 (b)(1)(ii) and OSHA 29 CFR 1926.405 (a)(2)(ii)(G).
Contact us to request pricing, availability and customization optionsContact Us
|Type||E-11 GFP - UL 943 Category FTTJ2 when used in tandem with Airpax LEL series UL 489 listed circuit breaker with shunt trip|
|Operating Voltage||120 VAC or 120/240 VAC|
|Interrupting Voltage||Rating of UL 489 listed circuit breaker|
|Sensing Coil Voltage Limit||600 VAC maximum|
|Phase Interrupt||Single (120 VAC 3 wire) and Split (120/240 VAC 4 wire)|
|Interrupting Current||Rating of UL 489 listed circuit breaker|
|Trip Time of Combined Assembly||100mS or less (60mS nominal)|
|Trip Level||5mA +/- 1mA|
|Operating Temperature||-35°C to +66°C|
Automatic on power up
1. Manual configuration should be specified if automatic start-up after power restoration of circuit power creates an unsafe condition.
2. As per UL 943 requirements, portable devices may require breaking of neutral during ground fault detection. Please contact the factory.
3. Please contact Airpax for optional ELCI, UL 1053 compliant devices.